FM 200 systems consist of the following components and their associated accessories:
FM-200 Storage Components – Storage components consist of the cylinder assembly(s), which contains the FM-200 chemical agent, and the cylinder bracket(s), which holds the cylinder assembly securely in place.
FM-200 Distribution Components – Distribution components consist of the discharge nozzles used to introduce the FM-200 into a protected hazard along with the associated piping system used to connect the nozzles to the cylinder assembly.
Trim Components – Trim components complete the installation of the FM-200 system and consist of connection fittings, pressure gauge, low-pressure supervisory switch, electric valve actuator, and manual valve actuator.
Slave Arrangement Components – Slave arrangement components consist of the pneumatic valve actuator(s), actuation check valve, vent check, actuation hose, and fittings required for a multiple cylinder (slave) arrangement.
Supplemental Components – Supplemental components include the discharge pressure switch and manifold check valve. They supplement the core equipment or complete a specific multi-cylinder configuration.
Control Panel – This device monitors the condition of the electric actuator, detectors, warning devices, cylinder pressure, and any manual release and abort stations. All electric or electronic devices must connect to the control panel in order to function.
Early Warning Detection and Alarm Devices – Early warning detection devices coupled with manual release and abort stations maximize system efficiency while audible and visual alarm devices alert staff of alarm conditions.