Emergency Generators Tests.
Tests would include full visual inspection, safety check, functional and performance test for the emergency generator installation. The tests shall include measurement on noise confirming compliance with the statutory requirements and/or as required by the Environmental Protection Department.
Emergency generators for fire service installation shall be located in separate room unless otherwise agreed.
After full test of the fire service installations in a building or premises have been carried out, with all systems connected to the mains electricity supply, the mains electricity supply shall be switched off to simulate power failure and the emergency generator shall start automatically.
During this period, the performance of each fire service installation shall be monitored and recorded. After the testing, the emergency generator set shall be examined and all instruments, safety devices cialisfrance24.com etc. shall indicate normal running of the generator. Finally the fuel tank shall be topped up-to the default initial level.